Symptom 1: Unit Will Not Start
NOTE: All repairs to the unit should be done by qualified service personnel. (i.e., for refrigeration, a licensed refrigeration mechanic, for electrical, a licensed electrician etc.) For mechanical repairs please call our main company telephone number which is monitored 24 hours, seven days a week.
Safety controls are set for water Operation (45° F. L.W.T.). For lower operating temperatures glycol must be used and controls must be reset by qualified personnel.
|9.1.1||Power off||1. Check main disconnect.|
|9.1.2||Main line open||2. Check fuses|
|9.1.3||Loose terminals||3. Tighten terminals with "POWER OFF"|
|9.1.4||Water Flow light not on.||4. See Section 9.7.1,2,4.|
|5. Failed flow switch. Have switch checked, repair or replace if defective.|
|9.1.5||6. Check control voltage fuses and transformer.|